Prices incl. VAT plus shipping costs
Delivery time 3 weeks
- Order number: LT-03135
The mobile system separator B-FW should prevent from flow back extinguishing water into the drinking water supply when the pressure in this network is lower than in the laid extinguishing water pipe. A volume flow of 1600 l/min at PN 16 and a maximum pressure loss of 1 bar are basic requirements for a fire service system separator.
The system separator B-FW is connected to standpipes or above-ground hydrants without
integrated system separator for removing extinguishing water from the pipe network.
The AWG system separator B-FW meets the requirements of DIN 14346 and is lightweight
and at the same time compact. All individual parts are protected against corrosion. With the permanent identification of the system separator is i.a. the mounting direction specified in use.
• meets the requirements of DIN 14346
• corrosion-protected components
• input screen
• lightweight and compact
entrance: Storz 75 (B), rotatable
exit: Storz 75 (B)
flow rate: at least 1600 l/min at 1 bar pressure loss
maximum operating pressure: 16 bar
material: aluminum alloy anodized; stainless steel
dimensions (Ø x length): 126 x 220 mm
weight: 1.9 kg
mobile system separator, drinking water, water to drink, safety, secure